what happens if the dwell angle adjustment at the contact breaker gets smaller? or larger for that matter? is there some ballpark way of replacing the contact breaker without a dwell meter?
i'v also replaced the distributor cap and rotor abt 2 months ago but apparently, the contacts seem arced already. this can't be normal right? could a badly adjusted contact breaker be the cause of it? tks.